I took down the existing ceiling fan with light fixture and put up a simple light fixture w/out a fan. The fan/light was controlled by one switch, with simple wiring (one black and one white wire). When I turned the breaker back on, the light came on, yay, but now the light won't turn off.
The wiring from the ceiling consists of two black, two white, and a ground...the wiring in the new light fixture also has two white, two black, and a ground wire.
How should these be connected?
You need to know which cable is the power feed and which cable runs to the switch. As far as the light fixture is concerned the 2 blacks and the 2 whites connect together. Then the whites are connected to the white from the power feed cable. Then the black power feed cable connects to the black wire from the switch,and the white wire from the switch connects to the 2 blacks from the fixture.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!