I have 8 dual bulb F32T8 fluorescent fixtures in soffits
illuminating my living room.
They are wired in parallel and
actuated by a 2-pole wall switch. I propose to rewire them so that one bulb of each fixture is on one circuit,
and the other bulb of each is on a second circuit. The wall
switch would become 3-pole:
low (power one circuit),
high (power both circuits),
off. To do that, I would
reroute one B+ lead (blue)
and one B- lead (red) to
a bulb in an adjacent box.
The high tension leads would run box-box in a flex steel conduit. The line voltage wiring would run through separate punch outs.
I'm aware that any jumper wiring would have to be 600DCV rated. The result
is 4 ballasts powering 8
tubes on one circuit, and 4 ballasts powering 8 tubes
on the other circuit, one tube in each box on circuit
A and the other tube on circuit B. Of course, they're really not separate circuits; they're joined at the switch. Are there any
code issues with this?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!