Switching out a ceiling fan for a regular light
I have removed a ceiling fan\light and am now trying to install a simple light, however, I am running into a problem. I turned off power to the room and turned the switch off. I detached the green ground, the white from white & black from black & blue from blue on ceiling fan, to remove it. The new light has 2 black wires & green ground. See pic attached. When I attached one black to white and other black to black and just capped the blue & green to green. I switched the power on (switch was in the off position on the wall)and the light came ON. My dilemma is that the switch does not turn the light on or off?? Please help.
HI. Yes you need to cap off the black from the ceiling (which is constant) and connect the light to the blue (which is controlled by the switch). Make sure the blue connects to the light socket's center tab (hot) and the white to the outside (neutral).
ceiling fan problem
Ceiling Fan Wiring, 2 hots
Encon Light with 3-speed Ceiling Fan motor capacitor...
Wiring is Black to White? What..?
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects