HI. I am about half way through putting walls up in my basement. I am using 2 X 3 studs and running electrical wires though with nails plates and so on. I know its to late now but is there any issue that I am using 2 X 3 studs and not 2 X 4 studs?
Most areas use the NEC (National Electric Code) to regulate electrical constructon. The NEC requires that sheathed electrical cable or type NM cabling (I assume that you are not installing wire in metal conduit) be no less than 1.25 inches from the nailable face of a stud or joist. This includes the backside of the stud or joist even if you are not finishing that side (like above the ceiling). This is to prevent nails being driven into the conductors. Deducting 1.25 inches from EACH face of a 2x4 stud (3.5" deep minus 1.25" minus 1.25") leaves room for a 1 inch hole to run conductors. Since 2x3 studs are only 2.5" deep, any hole for conductors would be closer than 1.25" to the surface. Fortunately the NEC allows holes closer than 1.25" if you add a UL approved steel plate over the face of the stud before installing the drywall. The plates are about 1.5" x 3" x 12 gauge and have nail tangs so you won't need nails. They are available at electrical suppliers and home builder stores.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!