I removed a ceiling fan/light and replaced it with a new light fixture. Unfortunately, I didn't note the wiring connections in the old fixture. The light won't turn on when the wall switch for it is moved to 'on'. The switch only controls this one fixture or, that is, it used to.
In the metal ceiling box: one cable - blk, wht, copper. I connect like colors to each other with good wire nuts and the copper wire from both cable and fixture to green screw.
In the metal switch box: one cable - blk, wht, copper. White wire at bottom of single pole switch is hot when measured to box. Blk wire at top of switch is not hot in 'off', becomes hot in 'on'. Copper wire is connect to green screw in box but NOT to switch.
I suspect some sort of non-standard circuitry here. It wouldn't be a surprise in this house.
Problem installing new light fixture with old switch...
installing ceiling fixture
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!