I removed a ceiling fan/light and replaced it with a new light fixture. Unfortunately, I didn't note the wiring connections in the old fixture. The light won't turn on when the wall switch for it is moved to 'on'. The switch only controls this one fixture or, that is, it used to.
In the metal ceiling box: one cable - blk, wht, copper. I connect like colors to each other with good wire nuts and the copper wire from both cable and fixture to green screw.
In the metal switch box: one cable - blk, wht, copper. White wire at bottom of single pole switch is hot when measured to box. Blk wire at top of switch is not hot in 'off', becomes hot in 'on'. Copper wire is connect to green screw in box but NOT to switch.
I suspect some sort of non-standard circuitry here. It wouldn't be a surprise in this house.
Problem installing new light fixture with old switch...
installing ceiling fixture
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 16 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects