I removed a ceiling fan/light and replaced it with a new light fixture. Unfortunately, I didn't note the wiring connections in the old fixture. The light won't turn on when the wall switch for it is moved to 'on'. The switch only controls this one fixture or, that is, it used to.
In the metal ceiling box: one cable - blk, wht, copper. I connect like colors to each other with good wire nuts and the copper wire from both cable and fixture to green screw.
In the metal switch box: one cable - blk, wht, copper. White wire at bottom of single pole switch is hot when measured to box. Blk wire at top of switch is not hot in 'off', becomes hot in 'on'. Copper wire is connect to green screw in box but NOT to switch.
I suspect some sort of non-standard circuitry here. It wouldn't be a surprise in this house.
Problem installing new light fixture with old switch...
installing ceiling fixture
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 10 Clever Uses for the Space Under the Stairs
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- House Quiz: Test Your Knowledge of U.S. Architecture
- 10 Things You Can Build with Plumbing Pipes
- Sweet Dreams: 16 Inventive Beds You Can Make Yourself
- Kitchen Envy: 10 Rooms We Love
- 16 Ingenious IKEA Hacks
- 18 Clever and Easy DIY Ways to Use Rope at Home
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 9 No-Sew Fabric DIY Projects to Dress Up Any Room
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight