Adding new light fixture to existing 3-Way wiring
If that's the case, you should be able to determine which wires from switch 2 are being used at the existing fixture and connect to the same ones for the new fixture.
I believe you've taken one connection for the new light from the wrong side of switch 1. Take it from the common.
If I read you right, there is a 2wire to switch 1, a 3wire from switch 1 to switch 2, and a 2wire from switch 2 to the existing fixture. Is this correct? If so, you should not be connecting any of the wires from the 3wire to the new fixture. That will result in "mixed-up" operation.
Whichever switch has the wire going from it to the existing fixture is the one you gotta get to the new fixture.
Another way to think of it is that both fixtures must be on the same "side" of the switches. And neither may be "between" the two switches. I'll try to illustrate below.
.. | . |
.. | . |
.. | . |
The two fixtures must be wired in parallel rather than in series relative to each other.
[This message has been edited by rpxlpx (edited January 21, 2003).]
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love