Weep Holes in Brick
I do not recommend you fill them or you could be causing an even bigger problem.
The method used to find out if there is flashing behind the brick depends on the type of weep hole they used. If they just left the head joints in the mortar open you can usually use a flash light. An even better way is to take a close up picture using a digital camera and flash. A third option is to probe with a piece of wire like a cut off coat hanger, but be careful not to puncture the flashing.
If they used a pre made plastic tube you will not be able to see the flashing but you may be able to probe for it. I most cases the flashing will be black vinyl or rubber, or asphalt impregnated fabric over copper.
The problem is that there is no way to tell if the flashing was installed properly without removing some brick. If the flashing has a hole in it, is too short, or is not damned up on the ends, you could have a problem.
Is there a metal drip cap over the window molding but underneath the brick? If there is (and there should be) it should be sealed to the wall sheathing behind the brick so even if the brick did leak it would prevent water from getting to the inside. This would be the first place I would suspect water problems.
I would suggest you make certain that all the other possible points of entry are sealed first. Then you may want to consider pursuing the flashing as a last resort.
Thanks again for the helpful hints. Tapping and looking into the weep hole I hit the piece of L steel that the brick is resting on over the window. It does not appear that anything is covering the steel to seal it. I tried spraying various points around the window with a hose to determine where the leak originates from, but the window would not leak. I guess I am at the point of removing brick. Mold is a big problem here in San Antonio and this would certainly bring that on.
[This message has been edited by seuhus (edited September 13, 2003).]
I will pull everything out of the weep holes.
Document this whoile process. You may need to further this calimn later
At the back of the house we have had a conservatory installed, unfortunately this means that 3 weep holes now exit inside the conservatory, in heavy rain we now have water running down the walls from the weep holes inside the conservatory.
Help - is there anyway to divert this water, or should we get the weep holes now exiting in the conservatory blocked up, if we block remove them, should we have additional ones installed outside area of conservatory.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!