There is a sewer odor coming from our bathroom sink drain. I don't smell it from any other drain in the house(we have 7 bathrooms + kitchen). What does this mean? Is it a problem with the septic system or the drain? We've had this house for about 6 months and it was vacant for a few years before we bought it. Any ideas?
Under your sink, make sure you have a "trap". This is a "S" turned on it's side. It alway's has water in it to prevent the odor from the main line comming back up to the sink.
Check your vent stack for the bath sink. I bet it is stopped-up. When it stops-up, the water flow from the sink actually siphons the water out of the "P" trap and leaves it open for the sewer gas to enter the room through the sink drain. If you are comfortable climbing, get a ladder and go the the vent pipe where it goes through the roof (should be in reasonable proximity to the sink). Take a garden hose, stick it down the vent a few feet and turn on the water. If the water backs up you will need to "snake it out". This should solve your prob. If you're lucky, the force of the water will unstop it for you.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!