I was using my garbage disposal upstairs, everything seemed to be draining fine. I happened to come down to the basement and could hear water. I went into the basement bathroom and water was coming up through the sink, along with the bits of broccoli I put into the garbage disposal.
The problem you describe sounds like wet venting. The drain line for your kitchen sink is also serving to vent your basement sink. If a clog forms downstream of the basement sink, water from the kitchen or basement could back up to the lowest elevation drain. Chances are the basement sink was just tied into the kitchen drain line some years ago. Depending on local code, this was probably not a legal connection, but it was functional. I suspect you have a partial clog in that drain line, at or upstream of the main. Time for a snake. If you can, I recommend installing a cleanout at the basement sink drain or vent.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!