I read in the Fix It For'em that the plumbing for my kitchen sink should be done as follows:
a sanitary tee in the wall behind the sink with the vent attaching to the top inlet and the trap arm to the branch.
But it is not. My drain comes up out of the floor, makes a 90 deg. turn towards the front of the cabinet, where the trap is atttached. so the only venting is through the sink drain.
How do I correct this?
It may be plumbed correctly...Is the sink directly in front of a window, if so the vent pipe maybe wet vented, with the vent pipe being in the wall close by. Do you smell sewer gas? does the sink drain properly (and others in the house)? If you are clear on both of those issues, I wouldn't worry. However you can install an AAV on the horizontal pipe leading to the trap. Just make sure it is 4" above the horizontal pipe. If you can't find an AAV at your store, they are available on line. Not all inspectors buy off on these, but they have been used in Europe for many years and are approved by international code.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!