My Utica boiler is exceeding 80 psi water pressure at 180 Deg. My expansion tank,circulators,pressure relief valve will then leak. I shut off the water supply and the boiler will shut off at about 23 psi. I turn the water back on and each successive cycle causes a higher and higher water pressure. I adjusted the aquastat down to 150 deg. but each cycle the prssure is greater. Any thoughts would be appreciated.
80 psi? The relief valve should relieve at 30 psi. You may have a faulty fill valve that's passing or the automatic feed is bad. Put your ear to the copper pipe that supplies water to the boiler to see if you can hear water. Normal pressure should be between 12 and 15 psi.
I have just changed the autofill valve and turned the water supply back on. The first cycle water pressure went to 35 and temp to 180 before cycling off. As soon as I turned on the water the expansion tank relief valve on top bled water. Expansion tank problem?
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- 10 Planters You Can Make Out of Everyday Things
- 21 "Expert Picks" for Fail-Safe Colors
- Garden Paths: 12 Easy-to-Imitate Stone Walkways
- 20 Ways to Make a Small Bathroom Big
- 9 Incredible Faux Finishes Possible with Paint
- 10 Sly Spots Where You Can Stash Your Storage Stuff
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight