My Utica boiler is exceeding 80 psi water pressure at 180 Deg. My expansion tank,circulators,pressure relief valve will then leak. I shut off the water supply and the boiler will shut off at about 23 psi. I turn the water back on and each successive cycle causes a higher and higher water pressure. I adjusted the aquastat down to 150 deg. but each cycle the prssure is greater. Any thoughts would be appreciated.
80 psi? The relief valve should relieve at 30 psi. You may have a faulty fill valve that's passing or the automatic feed is bad. Put your ear to the copper pipe that supplies water to the boiler to see if you can hear water. Normal pressure should be between 12 and 15 psi.
I have just changed the autofill valve and turned the water supply back on. The first cycle water pressure went to 35 and temp to 180 before cycling off. As soon as I turned on the water the expansion tank relief valve on top bled water. Expansion tank problem?
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING