My Utica boiler is exceeding 80 psi water pressure at 180 Deg. My expansion tank,circulators,pressure relief valve will then leak. I shut off the water supply and the boiler will shut off at about 23 psi. I turn the water back on and each successive cycle causes a higher and higher water pressure. I adjusted the aquastat down to 150 deg. but each cycle the prssure is greater. Any thoughts would be appreciated.
80 psi? The relief valve should relieve at 30 psi. You may have a faulty fill valve that's passing or the automatic feed is bad. Put your ear to the copper pipe that supplies water to the boiler to see if you can hear water. Normal pressure should be between 12 and 15 psi.
I have just changed the autofill valve and turned the water supply back on. The first cycle water pressure went to 35 and temp to 180 before cycling off. As soon as I turned on the water the expansion tank relief valve on top bled water. Expansion tank problem?
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects