I have a trilevel with an electric forced air furnace in the lower level. Lots of heat comes to the main floor, but virtually none to the other levels. Even with the registers closed in the rest of the house virtually no hot air comes upstairs. My furnace maintenence person told me that there is no way to diagnose or fix this problem without tearing the walls apart. Does anyone have any more helpful, less expensive ideas?
Installing dampers might help. The registers alone, don't function as a damper because they are on the end of a run. With dampers you will be able to adjust the air flow right at the source, the plenum or supply trunk.
You need to find a contractor who is experienced in TAB work. That is Testing Adjusting and Balancing. They can take air readings at different places to find out where the air is going. They can look at your equipment to see if it is sufficient to do what you require. There are many avenues to air flow related problems. There are no quick fixes. Start to find a contractor by looking here. Good luck.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects