I have a Lennox G51MP furnace. Just built this house last year and the furnace was installed in November, 3 months ago.
Last night, it was 0 degrees out. When my wife woke up me for work, she said "its feezing". When I went down stairs, the thermostat said 51. The furnace obviously shut off in the middle of the night. And, my wife babysits a 3 month old everymorning.
Luckily, I put a set of gas logs in when I built my house, so I quickly got them burning and within an hour the living room was toasty. However the basement is freezing as well as the upstairs.
I got out my manual from lennox and read the trouble shooting guide.
When the furnace first comes on, both the Red and Green LEDs blink fast, which the manual indicates as normal operation.
It goes through this cycle and then attempts to light... You see the pilot light come on, then a flame, then the flame goes out.
It does this seeral times for about 3-4 minutes then finally shuts down altogether.
Now, A different code come up. Alternating slow flashing red and green. The manua indicates the follwing.
"Watchguard-Burners failed to ignite, limit open longer than 3 minutes, or flame sense lost 5 times in one heating cycle."
Can anybody tell me what I need to do to fix it????
Is there a part that is malfunctioning?
Please, if you know the cause of this, give me some advice.
My furnace guy is out of town until monday.
If your lucky and it isn't a failed electronic part you can check a couple of things. Make sure your vent pipe an dintake pipe are clear. The drain hose is not kinked and then turn the switch off at the furnace and tighten any connections that you see inside the furnace. Just repaired my brothers furnace two nights ago and it was loose connections on a relay.
Good luck and stay warm.
Good luck and stay warm.
Either a bad flame sensor, or bad connection at the flame sensor. Make sure you have a good ground to the unit and you may check the polarity to the furnace, sometimes the ignition control will work with reversed polarity until the flame starts, then the electrical curent flows through the sensor improperly and flame rectification does not occur.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Top 11 Color Trends to Follow in 2014
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Laundry Room Ideas to Knock Your Socks Off
- 10 “Stone Sober” Household Uses for Liquor
- 10 Plant Containers to Make with Everyday Items
- 15 Spring Home Maintenance Musts
- 20 Ways to Make a Small Bathroom Big
- 12 Easy Ways to Revitalize Outdoor Furniture
- 14 Room Dividers to Organize Your Space
- Wow-Worthy Window Films: 11 Top Picks
- 10 Houseplants to Improve Air Quality
- 10 Ingenious Home Uses for Baking Soda