I am redoing the basement . When i removed the "old" paneling i found no insulation on the block walls. I decided to to build out the walls with 2x3's to save some space. The hot water baseboard runs to close to the walls to build them out, can i cap off the water to the basement ( seperate zone ) while building the wall and finishing ?. I would like to install new baseboard anyway.
And should i drain the entire system? i am having pop off problems also . Any help will be appreciated . Thanks in advance.
If the boiler is popping the relief valve it means 1) the automatic fill valve is letting too much water into the system 2) the expansion tank needs to be drained 3) you might have a bad relief valve. The boiler should run normal at about 15-20 psi on the gauge and about 180 deg. water temp. More than 30 psi or 220 deg. will open the relief valve. Of course you can drain the system to replumb the basement. You will need to vent all the radiators when you refill the system.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!