GFCI Breaker vs. Outlet
The concept behind a GFCI is simple: create a circuit that is highly sensitive to overload, to use in areas where water is present, so that the circuit will trip before harm is done. Normal circuits, fine in dry environments, may not trip in time when in situations like a hair dryer and running water. GFCI‚Äôs will trip in something like ¬º second. Now, there is much more to them than this, but I just wanted you to get the general idea.
A GFCI breaker goes in your circuit panel, and protects everything on that branch circuit from the breaker out, including receptacles, light fixtures, and even the wire. A GFCI receptacle, on the other hand, can protect itself alone, or, if installed inline, all outlets and wire downstream of its location. When building a new home, a builder can choose either method to achieve the desired coverage because they can run the wire easily from one location to the next, through unfinished walls. The combinations can be endless. For example, my last home had one GFCI receptacle controlling all the kitchen outlets, another for all the bathrooms, and one in the basement controlling there, the garage, and all the outside outlets. My current home is older, so to bring it up to code, I installed a separate GFCI receptacle at each outside outlet and bathroom. By luck, I was able to put one in my kitchen, which is positioned in its circuit such that it covers all kitchen outlets.
Your situation is different. Your house is already finished, and the wires are where they are. Installing GFCI receptacle at each bathroom location would be the simplest, and should meet code requirements in your area. The breaker versions are more expensive, and you probably would not be able to get away with one since each bathroom is no doubt on a different circuit. Also, since your home predates GFCI‚Äôs, the company that made your circuit panel may no longer be in business, or if they are, they may not manufacture a GFCI breaker. Even worse, you home may still use fuses. GFCI receptacles are much more universal, and can even accommodate older wiring.
Sorry to be so long-winded, so I‚Äôll close with this: There are many different situations that can occur, and since I have never seen your home, I can only approximate and guess. The best advise I can offer is for you to get a professional opinion, unless you are really, really, really sure of what you are doing. A good source for recommendations is your local municipality.
Installing a GFCI Breaker
Neutral wire of GFCI breaker is stranded
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!