GFCI Breaker vs. Outlet
The concept behind a GFCI is simple: create a circuit that is highly sensitive to overload, to use in areas where water is present, so that the circuit will trip before harm is done. Normal circuits, fine in dry environments, may not trip in time when in situations like a hair dryer and running water. GFCI‚Äôs will trip in something like ¬º second. Now, there is much more to them than this, but I just wanted you to get the general idea.
A GFCI breaker goes in your circuit panel, and protects everything on that branch circuit from the breaker out, including receptacles, light fixtures, and even the wire. A GFCI receptacle, on the other hand, can protect itself alone, or, if installed inline, all outlets and wire downstream of its location. When building a new home, a builder can choose either method to achieve the desired coverage because they can run the wire easily from one location to the next, through unfinished walls. The combinations can be endless. For example, my last home had one GFCI receptacle controlling all the kitchen outlets, another for all the bathrooms, and one in the basement controlling there, the garage, and all the outside outlets. My current home is older, so to bring it up to code, I installed a separate GFCI receptacle at each outside outlet and bathroom. By luck, I was able to put one in my kitchen, which is positioned in its circuit such that it covers all kitchen outlets.
Your situation is different. Your house is already finished, and the wires are where they are. Installing GFCI receptacle at each bathroom location would be the simplest, and should meet code requirements in your area. The breaker versions are more expensive, and you probably would not be able to get away with one since each bathroom is no doubt on a different circuit. Also, since your home predates GFCI‚Äôs, the company that made your circuit panel may no longer be in business, or if they are, they may not manufacture a GFCI breaker. Even worse, you home may still use fuses. GFCI receptacles are much more universal, and can even accommodate older wiring.
Sorry to be so long-winded, so I‚Äôll close with this: There are many different situations that can occur, and since I have never seen your home, I can only approximate and guess. The best advise I can offer is for you to get a professional opinion, unless you are really, really, really sure of what you are doing. A good source for recommendations is your local municipality.
Installing a GFCI Breaker
Neutral wire of GFCI breaker is stranded
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 9 Expert Furniture Arranging Tips
- 16 Inventive Beds You Can Make Yourself
- World's Most Amazing Slip 'N Slide
- 13 Lanterns For Your Porch, Patio, or Garden
- 133 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 16 New Ways to Store Kitchen Necessities
- 12 Garden Sheds You Could Live (or Work) In
- 11 Big Ideas for Small Kitchens
- 47 Industrial Kitchens
- 283 Great DIY Project Ideas
- The Right Path: 15 Wonderful Walkway Designs
- Laundry Room Ideas to Knock Your Socks Off
- 17 Backsplashes for a Unique Kitchen
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in a Day
- Easy DIY Fixes for 11 Annoying House Problems
- Capitalize on Your Attic: 10 Inspirations
- 14 Room Dividers to Organize Your Space
- 10 Creative New Ways to Use Old Bottles
- Make Good Use of Old Junk: 14 Creative Ideas
- 22 Tiny Houses We Love
- 10 Smart Solutions for Small Bedrooms
- 5 DIY Porch Swings Perfect for Summer
- 1 Dozen Ways to Maximize a Small Yard
- 20 Ways to Make a Small Bathroom Big
- 5 Easy and Creative DIY Lamps