GFCI Breaker vs. Outlet
The concept behind a GFCI is simple: create a circuit that is highly sensitive to overload, to use in areas where water is present, so that the circuit will trip before harm is done. Normal circuits, fine in dry environments, may not trip in time when in situations like a hair dryer and running water. GFCI‚Äôs will trip in something like ¬º second. Now, there is much more to them than this, but I just wanted you to get the general idea.
A GFCI breaker goes in your circuit panel, and protects everything on that branch circuit from the breaker out, including receptacles, light fixtures, and even the wire. A GFCI receptacle, on the other hand, can protect itself alone, or, if installed inline, all outlets and wire downstream of its location. When building a new home, a builder can choose either method to achieve the desired coverage because they can run the wire easily from one location to the next, through unfinished walls. The combinations can be endless. For example, my last home had one GFCI receptacle controlling all the kitchen outlets, another for all the bathrooms, and one in the basement controlling there, the garage, and all the outside outlets. My current home is older, so to bring it up to code, I installed a separate GFCI receptacle at each outside outlet and bathroom. By luck, I was able to put one in my kitchen, which is positioned in its circuit such that it covers all kitchen outlets.
Your situation is different. Your house is already finished, and the wires are where they are. Installing GFCI receptacle at each bathroom location would be the simplest, and should meet code requirements in your area. The breaker versions are more expensive, and you probably would not be able to get away with one since each bathroom is no doubt on a different circuit. Also, since your home predates GFCI‚Äôs, the company that made your circuit panel may no longer be in business, or if they are, they may not manufacture a GFCI breaker. Even worse, you home may still use fuses. GFCI receptacles are much more universal, and can even accommodate older wiring.
Sorry to be so long-winded, so I‚Äôll close with this: There are many different situations that can occur, and since I have never seen your home, I can only approximate and guess. The best advise I can offer is for you to get a professional opinion, unless you are really, really, really sure of what you are doing. A good source for recommendations is your local municipality.
Installing a GFCI Breaker
Neutral wire of GFCI breaker is stranded
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- 142 Remarkable Houses Around the World
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers
- 159 Smart Storage Ideas for the Whole House
- 10 Room Dividers to Bring Order to Your Space
- Shelf Life: 10 Bookcase Projects You Can DIY
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- 11 Amazing Homemade Sheds to Inspire Your Own
- Pest, Be Gone! 10 Steps to a Critter-Free Home
- 17 Design Inspirations for Mudrooms and Entryways
- Recipe for Success: 10 Easy Kitchen Storage Hacks
- Laundry Room Ideas to Knock Your Socks Off
- Winning Combinations: 9 "Can't Miss" Color Schemes
- Secret Rooms: 10 Special Spaces Hidden from Sight