Kitchen Outlets Blow Fuses
After I hooked up the outlets I inserted the devices that house the fuses into the fuse box and turned the power back on. All four fuses blew. The windows in the fuses were black (which I have read indicates a short somewhere). I took all of the wires off of the outlets and inserted new fuses again. This time the fuses did not burn out (without the wires being connected to the outlets). Each of the outlet boxes has a black, a red, a white and a ground wire. I tested the wires for incoming power and found this to be true for the blacks and the reds. Could someone tell me where I am going wrong? If I can't solve this I will call an electrician but if it is something simple I would like to try. Thanks
This is the same set up as my parents kitchen outlets at their house. I checked to make sure.
My guess is the original installer wanted two seperate circuits to run the kitchen appliances and they are sharing the neutral wire. Try connecting just the black and white wires to the outlets and see if the fuses hold.
Let me know what happens and I'll take you from there. Don't want to give you information that will not help.......
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!