I cant get the thing to work. I used 2-wire cable. At first I ran the hot back from the switch through the fixture to the next fixture to neutral. Both lights were very dim and I realized my mistake.
I then ran another single wire between the two fixtures (making it a 3-wire segment)to use as the neutral from the first fixture, and then pigtailed the power from the switch to both the fixtures singularly. This didnt work at all. In fact, both fixtures were on dimly with the switch in the OFF position, and when the switch was on, only the second fixture back from the switch lit up.
Any ideas on what I am doing wrong? I would appreciate any advice, but especially any references where I could see a diagram of such a configuration.