Electrical Dryer outlet
This meant that @ 240volts there was Hot-Hot-Ground.
The problem was that ranges and dryers began evolving many 120vac assessories, lights, timers, bells, whistles , etc....
This meant current was 'returning' on the grounding conductor. Granted, a negligible qantity at first, but increasingly so, thus this introducing a hazard.
So it became a code ( i'm thinking the 93' or 96' cycle without looking) to have a 4-prong receptacle and 'pigtail'
( cord from unit).
so now we have Hot-Hot-Nuetral-Ground
This is not so far fetched if one considers the modern day receptacle that has Hot-Nuetral-Ground ( looks like a face with the ground down)
There is a real hazard with the Three (3) conductor cord-sets by using the Neutral for both the neutral and the equipment grounding conducor. Especially since the motor is 120 volts, if by chance you lose the neutral, albeit loose, broken or if it comes apart, the whole appliance will be energised and can become a serious shock hazard.
Be careful and be safe.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects