Electrical Dryer outlet
This meant that @ 240volts there was Hot-Hot-Ground.
The problem was that ranges and dryers began evolving many 120vac assessories, lights, timers, bells, whistles , etc....
This meant current was 'returning' on the grounding conductor. Granted, a negligible qantity at first, but increasingly so, thus this introducing a hazard.
So it became a code ( i'm thinking the 93' or 96' cycle without looking) to have a 4-prong receptacle and 'pigtail'
( cord from unit).
so now we have Hot-Hot-Nuetral-Ground
This is not so far fetched if one considers the modern day receptacle that has Hot-Nuetral-Ground ( looks like a face with the ground down)
There is a real hazard with the Three (3) conductor cord-sets by using the Neutral for both the neutral and the equipment grounding conducor. Especially since the motor is 120 volts, if by chance you lose the neutral, albeit loose, broken or if it comes apart, the whole appliance will be energised and can become a serious shock hazard.
Be careful and be safe.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- 10 Planters You Can Make Out of Everyday Things
- 21 "Expert Picks" for Fail-Safe Colors
- Garden Paths: 12 Easy-to-Imitate Stone Walkways
- 20 Ways to Make a Small Bathroom Big
- 9 Incredible Faux Finishes Possible with Paint
- 10 Sly Spots Where You Can Stash Your Storage Stuff
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight