Moving a Breaker Box
Basic rules require headroom at working spaces near service equipment, switchboards, panelboards, or motor control centers to be not less than 6¬Ω ft.
However, in existing dwelling units, service equipment or panelboards rated at not over 200 amperes are allowed in spaces where the headroom is less than 6¬Ω ft.
Note: This rule that was really added to the code to address so-called "pre fabricated homes" now called "manufactured homes" and the lack of space for the service equipment.
Additional comments encouraged.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Top 11 Color Trends to Follow in 2014
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers