number of pigtails in a 5 gang outlet under NEC
The number of conductors allowed in the box that is stamped inside the box refers to the total capactity of that box to contain that number of current carrying conductors. However that stamped number in that box does not allow for any reductions for devices, equipment grounding conductors, straps, hickeys, etc. that also must be counted as current carrying conductors.
NEC 370-16-b states approximately the following, more is said in that article but this is the basics.
14 Ga wires must be provided 2 cubic inch of box capacity for each current carrying conductor in that box. 2.25 cubic inch is required for 12 ga wire.
It goes further to say that you must deduct one current carrying conductor for all the bare or green wires in that box as a total of one conductor reduction to you capacity of that box.
A device must deduct 2 current carrying conductors for each yoke [mounting bracket of each recepacle, switch, etc.
A strap or clamp that enters the box 1/2" must also deduct 1 current carrying conductor for a total of all straps in that box counted as one deduction.
A pigtail that originates within that box but does not leave that box is not counted as a current carrying conductor.
Any wire that enters or leaves that box whether wire nutted together or not must be counted as one conductor for each entry or exit with the exception of the rule for green or bare wires.
Any wire that passes through that box but is not cut in that box is only counted as one.
A few other rules apply and are in 370-16 but those are the main rules of this subject.
The above calculation method applies to any conductors 14 ga through 6 ga.
Any box containing #4 or larger conductors must be counted by a different method due to there size.
Hope this helps
I would "make 2 or 3 pigtails and connect them" as you suggested.
One more thing... If you have nothing else on that circuit, you shouldn't need 12 guage wire - 14 would do, and it's much easier to work with.
[This message has been edited by rpxlpx (edited March 13, 2001).]
How to install a deck over looking a pond
Hydronic Heat, Indirect Water Heater, No Hot Water, ...
turn $6 into $6000
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!