number of pigtails in a 5 gang outlet under NEC
The number of conductors allowed in the box that is stamped inside the box refers to the total capactity of that box to contain that number of current carrying conductors. However that stamped number in that box does not allow for any reductions for devices, equipment grounding conductors, straps, hickeys, etc. that also must be counted as current carrying conductors.
NEC 370-16-b states approximately the following, more is said in that article but this is the basics.
14 Ga wires must be provided 2 cubic inch of box capacity for each current carrying conductor in that box. 2.25 cubic inch is required for 12 ga wire.
It goes further to say that you must deduct one current carrying conductor for all the bare or green wires in that box as a total of one conductor reduction to you capacity of that box.
A device must deduct 2 current carrying conductors for each yoke [mounting bracket of each recepacle, switch, etc.
A strap or clamp that enters the box 1/2" must also deduct 1 current carrying conductor for a total of all straps in that box counted as one deduction.
A pigtail that originates within that box but does not leave that box is not counted as a current carrying conductor.
Any wire that enters or leaves that box whether wire nutted together or not must be counted as one conductor for each entry or exit with the exception of the rule for green or bare wires.
Any wire that passes through that box but is not cut in that box is only counted as one.
A few other rules apply and are in 370-16 but those are the main rules of this subject.
The above calculation method applies to any conductors 14 ga through 6 ga.
Any box containing #4 or larger conductors must be counted by a different method due to there size.
Hope this helps
I would "make 2 or 3 pigtails and connect them" as you suggested.
One more thing... If you have nothing else on that circuit, you shouldn't need 12 guage wire - 14 would do, and it's much easier to work with.
[This message has been edited by rpxlpx (edited March 13, 2001).]
How to install a deck over looking a pond
Hydronic Heat, Indirect Water Heater, No Hot Water, ...
turn $6 into $6000
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 15 Fast Facade Fixes for Instant Curb Appeal
- 9 Expert Furniture Arranging Tips
- 16 Inventive Beds You Can Make Yourself
- 13 Lanterns For Your Porch, Patio, or Garden
- 5 Ways to Repurpose Old Window Screens
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 8 Classic Ways to Make a Small Room Look Big
- 8 DIY Storage Solutions for a Closet-less Room
- 9 Potent Cleaners You Didn't Know You Had
- 12 Hobbit Houses to Make You Consider Moving Underground
- 16 Cool DIY Coffee Tables
- 10 Fall Home Maintenance Musts
- Supersize Your Small Bath With These 8 Pro Tips
- 15 Neat Garage Storage Solutions
- Buy or Build: 15 Desks We Love
- 10 Great DIY Bookshelf Projects
- 5 Minutes Flat: 7 Upgrades You Can Do in Under 300 Seconds
- 10 Creative New Ways to Use Old Bottles
- 10 FREE Storage Hacks
- 10 New Uses for Old Doors
- 7 Ways to Make Your New House Look Old
- Soundproof Your Home with 11 DIYs
- Set the Tone: 8 Colors for an Inviting Dining Room
- 17 Mini Bars to Mix Up Your Home Decor
- 20 Ways to Make a Small Bathroom Big
- 10 Insanely Creative Shelves You Can DIY