GFI on a 3-way circuit?
Well the light works fine, but my circuit tester says my GFCIs have an open ground. By my thinking, I should have two potential grounds since this is a 3-way circuit. What I'm wondering though is do I actually have a problem with my nuetral since I'm trying to get power from a 3-way circuit. Also, can I fix my problem by just eliminating one of the swithces on my 3-way circuit?
I'm not pluggin the anything into a circuit that's not properly grounded, especially something that combine water AND electricity.
I appreciate any help, and do have most basic test equipment (circuit tester, voltmeter, etc.)
Just had another thought.. Some circuit testers might give "open ground" readings on GFI outlets because of the difference between them and "regular" outlets. Just for fun, try replacing temporarily with a "regular" outlet and see if it reads "open ground" with that tester.
[This message has been edited by rpxlpx (edited May 31, 2001).]
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!