We purchased a home built in 1930 that has several old 2-prong outlets. Our home inspector suggested we replace these with new 3 prong outlets. Is this a matter of simply going to the store getting replacements and wiring them in, or will the 2-prong outlets need to be rewired by an electrician.
You cannot simply replace them with the 3 prong outlet. The code does allow you to replace each one with a Gfi outlet and to label each one as having no equipment ground. If you are fortunate enough to have metal conduit running in your walls and completing a path to ground to your electrical panel than you can ground them to the metal box and/or pull in a ground wire back to the panel.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!