Circuit panel location
In dwelling units, and guest rooms of hotels and motels, overcurrent devices, other than supplementary overcurrent protection, are not allowed to be located in bathrooms.
Bathroom. An area including a basin with one or more of the following: a toilet, a tub, or a shower.
[This message has been edited by Joe Tedesco (edited September 30, 2002).]
If this is a storage closet then it would not qualify as the items would block access.
If there was a closet just deep enough to hold the panel and the door was wide enough than a closet would qualify.
But this is up to inspector interpretation.
Also they might concider it as part of the bathroom and disqualify it on that grounds.
Simple fix - close off the existing closet door, and create new door access through an unused closet wall to the hall.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!