Ground Fault Circuit Indicator
One other possibility is you wired the new GFCI incorrectly. There is a difference between line and load. Not all GFCI outlets have the identical "configutation". That is, some have the hot line at the top, others have it at the bottom. Same for the load hot.
At this point, I'd bring in an electrician. No offense, but electricity is dangerous and you have not grasped the basics yet.
BTW - the I stands for Interrupt, not indicator.
GFCI receptacle flaky?
Aging Electrical Wiring in the USA
Installing and Testing Ground-Fault Circuit-Interrup...
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Beginners
- 16 Inventive Beds You Can Make Yourself
- World's Most Amazing Slip 'N Slide
- 15 Once-Popular Items Now Vanishing
- 133 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 16 New Ways to Store Kitchen Necessities
- 12 Garden Sheds You Could Live (or Work) In
- 11 Big Ideas for Small Kitchens
- 5 Things to Do with... Colanders
- 283 Great DIY Project Ideas
- The Right Path: 15 Wonderful Walkway Designs
- Laundry Room Ideas to Knock Your Socks Off
- 17 Backsplashes for a Unique Kitchen
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in a Day
- Easy DIY Fixes for 11 Annoying House Problems
- Capitalize on Your Attic: 10 Inspirations
- 14 Room Dividers to Organize Your Space
- 10 Creative New Ways to Use Old Bottles
- Make Good Use of Old Junk: 14 Creative Ideas
- 22 Tiny Houses We Love
- 10 Smart Solutions for Small Bedrooms
- 5 DIY Porch Swings Perfect for Summer
- 1 Dozen Ways to Maximize a Small Yard
- 20 Ways to Make a Small Bathroom Big
- 5 Easy and Creative DIY Lamps