Ground Fault Circuit Indicator
One other possibility is you wired the new GFCI incorrectly. There is a difference between line and load. Not all GFCI outlets have the identical "configutation". That is, some have the hot line at the top, others have it at the bottom. Same for the load hot.
At this point, I'd bring in an electrician. No offense, but electricity is dangerous and you have not grasped the basics yet.
BTW - the I stands for Interrupt, not indicator.
GFCI receptacle flaky?
Aging Electrical Wiring in the USA
Installing and Testing Ground-Fault Circuit-Interrup...
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 16 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects