Ground Fault Circuit Indicator
One other possibility is you wired the new GFCI incorrectly. There is a difference between line and load. Not all GFCI outlets have the identical "configutation". That is, some have the hot line at the top, others have it at the bottom. Same for the load hot.
At this point, I'd bring in an electrician. No offense, but electricity is dangerous and you have not grasped the basics yet.
BTW - the I stands for Interrupt, not indicator.
GFCI receptacle flaky?
Aging Electrical Wiring in the USA
Installing and Testing Ground-Fault Circuit-Interrup...
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Picture-Perfect Patios: 10 Outdoor Spaces to Love
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers