Ground Fault Circuit Indicator
One other possibility is you wired the new GFCI incorrectly. There is a difference between line and load. Not all GFCI outlets have the identical "configutation". That is, some have the hot line at the top, others have it at the bottom. Same for the load hot.
At this point, I'd bring in an electrician. No offense, but electricity is dangerous and you have not grasped the basics yet.
BTW - the I stands for Interrupt, not indicator.
GFCI receptacle flaky?
Aging Electrical Wiring in the USA
Installing and Testing Ground-Fault Circuit-Interrup...
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 11 Signs of an Unhappy Houseplant
- Insanely Easy 60-Minute Home Improvements
- 10 Cool Shipping Container Homes
- 9 Perfect Color Combos for Your Home
- 22 Tiny Houses We Love
- See the Most Highly Anticipated Colors for 2015
- Assembly Required: 15 DIY Kit Homes
- Favorite Space-Saving Double-Duty Furniture
- 10 IKEA Favorites, DIY Style
- Redecorate Without Spending a Dime: 10 Ideas
- 10 Houseplants You Can Grow Anywhere
- 9 Amazing Mobile Home Makeovers
- 10 Doable Designs for a DIY Rug
- 9 Alternative Uses for Toothpaste
- Live Large in a (Very) Small Space
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips