Ground Fault Circuit Indicator
One other possibility is you wired the new GFCI incorrectly. There is a difference between line and load. Not all GFCI outlets have the identical "configutation". That is, some have the hot line at the top, others have it at the bottom. Same for the load hot.
At this point, I'd bring in an electrician. No offense, but electricity is dangerous and you have not grasped the basics yet.
BTW - the I stands for Interrupt, not indicator.
GFCI receptacle flaky?
Aging Electrical Wiring in the USA
Installing and Testing Ground-Fault Circuit-Interrup...
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING