I recently had central air installed and the electrician put the 4 circuit breakers in a now full 100 amp panel. The lights on that circuit dim whenever the ac cycles. We have a 200 amp panel also that is almost empty. Should'nt he have located these breakers in the 200 amp panel? Also should these breakers be located as close to the 200 amp main breaker as possible or does it not matter?
are the breakers installed all on the same side of the 100 amp. panel?..if so, the problem may be an unbalanced load in the panel. and, yes, it prolly would have been better to use the 200 amp. panel, and to divide the load between the busses, i.e. 2 0n the left bus and 2 on the right. a loose neutral can also cause the light dimming problem you indicate.
hope this helps!
hope this helps!
Adding a sub-panel to existing service/hot tub
recommended wire size for 100 amp service
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 8 Smart Shoe Racks You Can Make Today
- Insanely Easy 60-Minute Home Improvements
- 30 Things Every Adult Should Know How to Do
- 9 Things You Never Thought to Paint—But Should
- 12 Sheds You Could Live (or Work) In
- 16 Designs for a Low-Cost DIY Coffee Table
- Assembly Required: 15 DIY Kit Homes
- 10 Surprisingly Simple Woodworking Projects
- 9 Totally Amazing Mobile Home Makeovers
- Storage Where You Least Expected It
- 9 Best Lighting Picks for Your Bedroom
- 22 Tiny Houses We Love
- 9 Closet Storage Tips from a Pro Organizer
- See the Most Highly Anticipated Colors for 2015
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- 10 Alternatives to a Traditional Home Office