I recently had central air installed and the electrician put the 4 circuit breakers in a now full 100 amp panel. The lights on that circuit dim whenever the ac cycles. We have a 200 amp panel also that is almost empty. Should'nt he have located these breakers in the 200 amp panel? Also should these breakers be located as close to the 200 amp main breaker as possible or does it not matter?
are the breakers installed all on the same side of the 100 amp. panel?..if so, the problem may be an unbalanced load in the panel. and, yes, it prolly would have been better to use the 200 amp. panel, and to divide the load between the busses, i.e. 2 0n the left bus and 2 on the right. a loose neutral can also cause the light dimming problem you indicate.
hope this helps!
hope this helps!
Adding a sub-panel to existing service/hot tub
recommended wire size for 100 amp service
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING