I recently had central air installed and the electrician put the 4 circuit breakers in a now full 100 amp panel. The lights on that circuit dim whenever the ac cycles. We have a 200 amp panel also that is almost empty. Should'nt he have located these breakers in the 200 amp panel? Also should these breakers be located as close to the 200 amp main breaker as possible or does it not matter?
are the breakers installed all on the same side of the 100 amp. panel?..if so, the problem may be an unbalanced load in the panel. and, yes, it prolly would have been better to use the 200 amp. panel, and to divide the load between the busses, i.e. 2 0n the left bus and 2 on the right. a loose neutral can also cause the light dimming problem you indicate.
hope this helps!
hope this helps!
Adding a sub-panel to existing service/hot tub
recommended wire size for 100 amp service
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects