8-3 w/ground UF
I wired my house for a hot tub using 8-3 w/ground UF wire (from a 60 amp GCFI sub-panel to a 4hp hot tub motor). The inspector told me even if I have the UF wire in a conduit I have to bury it 12 inches. I bought PVC conduit pipe - it can be on top of the ground so why does it have to be buried? What does the NEC state as the requirement for the 8-3 UF wire from the sub-panel to the tub?
Direct burial cables (Type UF for example), must be buried 24" and non-metallic raceways (PVC) must be buried at least 18".
Your inspector is letting you off easy, your cable is too small for the breaker you are using. #8 cables should only be protected at 50 amps.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 16 Sneaky Storage Ideas
- 20 Easy 60-Minute Home Improvements
- 9 Ways to Troubleshoot the Furnace
- 11 Real Haunted Houses to Visit--If You Dare!
- 9 Alternative Uses for Toothpaste
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 8 Ways to Make a Small Room Look Big
- 21 Expert Picks for Fail-Safe Colors
- 10 Fall Door DIYs for the Best House on the Block
- The Cheapest Ways to Boost Home Value
- 10 New Uses for Old Doors
- 10 Unexpected Uses for Spray Paint
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 8 Amazing Handmade Kitchen Counters
- 10 New Uses for Old Dressers
- 7 Upgrades You Can Do in Under 300 Seconds
- 10 Thrifty DIY Ways to Organize Your Home
- 26 Easy Painted Pumpkins for Halloween
- 9 Totally Amazing Mobile Home Makeovers
- 5 "Make in a Weekend" Bookshelf Projects
- 3 New Ways to Decorate with Fallen Leaves
- 10 "Zero Dollar" Storage Hacks
- 121 DIY Ideas for Halloween
- The 10 Best Things to Buy Secondhand
- 16 Must-See Coffee Tables You Can DIY—Easily!