electrical grounding for garage
Make sure that there are no other conductive paths between your garage & house, otherwise you need to add an equipment grounding conductor from the hous to the garage and treat the panel in the garage like a sub-panel by keeping the neutral & grounds separated. You'll still need 2 ground rods at the garage.
[This message has been edited by Tom O (edited October 15, 2002).]
The first, you state that the inside panel is grounded to the water line. Sadly, this location is not the service, which is where the grounding is required.
The second, you state you want to tie the wires for the garage into the outside box, below the meter. You can only do this using approved connections. You cannot install two wires under one screw (unless approved), so additional work will be required to tie in your conductors at this location.
You really should get help with this. There are alot of variables involved, and omitting any one could spell disaster for you or your loved ones.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 8 Smart Shoe Racks You Can Make Today
- Insanely Easy 60-Minute Home Improvements
- 30 Things Every Adult Should Know How to Do
- 9 Things You Never Thought to Paint—But Should
- 12 Sheds You Could Live (or Work) In
- 16 Designs for a Low-Cost DIY Coffee Table
- Assembly Required: 15 DIY Kit Homes
- 10 Surprisingly Simple Woodworking Projects
- 9 Totally Amazing Mobile Home Makeovers
- Storage Where You Least Expected It
- 9 Best Lighting Picks for Your Bedroom
- 22 Tiny Houses We Love
- 9 Closet Storage Tips from a Pro Organizer
- See the Most Highly Anticipated Colors for 2015
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- 10 Alternatives to a Traditional Home Office