electrical grounding for garage
Make sure that there are no other conductive paths between your garage & house, otherwise you need to add an equipment grounding conductor from the hous to the garage and treat the panel in the garage like a sub-panel by keeping the neutral & grounds separated. You'll still need 2 ground rods at the garage.
[This message has been edited by Tom O (edited October 15, 2002).]
The first, you state that the inside panel is grounded to the water line. Sadly, this location is not the service, which is where the grounding is required.
The second, you state you want to tie the wires for the garage into the outside box, below the meter. You can only do this using approved connections. You cannot install two wires under one screw (unless approved), so additional work will be required to tie in your conductors at this location.
You really should get help with this. There are alot of variables involved, and omitting any one could spell disaster for you or your loved ones.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!