You say you're getting a reverse polarity indication, I assume this is at the refrigerator receptacle. If that is the case, take a close look at the terminals on the LOAD side of the GFI. Make sure you are connecting the correct wires to each terminal. Do not go by the color of the screws, look for the word "white" or "neutral."
Frequently, the load neutral is on the opposite side of the case as the line neutral & the same thing applies to the hot wires. This would result in a reverse polarity at the next receptacle if both of your white wires are on the same side of the GFI.
Hope I haven't confused you too much.
As for your other problem, how many wires are there at the refrigerator outlet and how many wires are at the GFI?
[This message has been edited by Tom O (edited October 21, 2002).]
GFI outlets keeps getting tripped by dishwasher door...
bonded neutrals and GFI annoyances
need help with GFI problem
Fridge tripping GFI outlets
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 16 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects