You say you're getting a reverse polarity indication, I assume this is at the refrigerator receptacle. If that is the case, take a close look at the terminals on the LOAD side of the GFI. Make sure you are connecting the correct wires to each terminal. Do not go by the color of the screws, look for the word "white" or "neutral."
Frequently, the load neutral is on the opposite side of the case as the line neutral & the same thing applies to the hot wires. This would result in a reverse polarity at the next receptacle if both of your white wires are on the same side of the GFI.
Hope I haven't confused you too much.
As for your other problem, how many wires are there at the refrigerator outlet and how many wires are at the GFI?
[This message has been edited by Tom O (edited October 21, 2002).]
GFI outlets keeps getting tripped by dishwasher door...
bonded neutrals and GFI annoyances
need help with GFI problem
Fridge tripping GFI outlets
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love