100 amp Sub-Panel Installation
Using #2 copper would avoid any problem with your inspector. If you use #2-3 with ground non-metallic sheathed cable, the ampacity is 95 amps, but there is a rule (240.4(B)(3))that allows you to round this up to 100 amps which is a standard size overcurrent device.
What do you mean by encased?
[This message has been edited by Tom O (edited November 12, 2002).]
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!