Peculiar Electric Antics
'The symptoms you describe, other than the wind, are classic signs of a loose neutral. This causes the voltage to go down on one of the hot phases while it goes up on the other phase. Your house wiring & old fashioned appliances can handle this fairly well, but your electronic equipment can be damaged.
My advice is to unplug any electronic equipment.. Get an electrician on site as soon as possible. I suspect that the loose neutral could be associated with the service drop to your house, possibly at the weatherhead. You might get the power company to check that and ask them to check inside the meter base.
Good luck, let us know the outcome.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 21 Expert Choices for Fail-Safe Paint Colors
- 20 Easy 60-Minute Home Improvements
- 10 IKEA Favorites Made New with Paint
- The Tiniest Appliances You Never Knew Existed
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 8 Ways to Make a Small Room Look Big
- Sweet Dreams: 15 Inventive Beds You Can Make Yourself
- 10 Fall Door DIYs for the Best House on the Block
- The Cheapest Ways to Boost Home Value
- 10 New Uses for Old Doors
- 26 Easy Painted Pumpkins for Halloween
- 15 Once-Popular Home Items Now Vanishing
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 7 Reasons to Reconsider Wallpaper
- 10 New Uses for Old Dressers
- 7 Upgrades You Can Do in Under 300 Seconds
- 10 Thrifty DIY Ways to Organize Your Home
- 12 "Different" Ways to Store Firewood
- 5 DIY Farm Table Projects That Will Last a Lifetime
- Beyond White: 11 Bathroom Paint Colors
- 10 DIYs for a Festive Front Door This Fall
- 10 Creative New Ways to Use Old Bottles
- The 10 Best Things to Buy Secondhand
- 16 Must-See Coffee Tables You Can DIY—Easily!