Peculiar Electric Antics
'The symptoms you describe, other than the wind, are classic signs of a loose neutral. This causes the voltage to go down on one of the hot phases while it goes up on the other phase. Your house wiring & old fashioned appliances can handle this fairly well, but your electronic equipment can be damaged.
My advice is to unplug any electronic equipment.. Get an electrician on site as soon as possible. I suspect that the loose neutral could be associated with the service drop to your house, possibly at the weatherhead. You might get the power company to check that and ask them to check inside the meter base.
Good luck, let us know the outcome.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects