Black 12 awg
white 12 awg
ground 14 awg
14 gauge ground wire
The installers evidently forgot that although they were doing more than required, they must still comply with all the rules, in this case, the equipment ground must be #12.( presuming that the #12 wire is connected to a 20 amp breaker, if it is connected to a 15 amp breaker, all is well).
There is some danger to this installation, but I can think of a lot of other things that are more hazardous. However, it is always best to be in complete compliance with the NEC, so I'd advise having this problem corrected.
This practice is no longer allowed. New work is required to follow new rules, so you only need to replace it when it is otherwise necessary in the course of remodeling, maintenance, etc.
I've been rewiring my old house for about 6 months now (off and on), and I run 12G wire on 15A circuits and add a 14G bonding wire if I have any concern about the mechanical connection. Is this the same issue?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love