Black 12 awg
white 12 awg
ground 14 awg
14 gauge ground wire
The installers evidently forgot that although they were doing more than required, they must still comply with all the rules, in this case, the equipment ground must be #12.( presuming that the #12 wire is connected to a 20 amp breaker, if it is connected to a 15 amp breaker, all is well).
There is some danger to this installation, but I can think of a lot of other things that are more hazardous. However, it is always best to be in complete compliance with the NEC, so I'd advise having this problem corrected.
This practice is no longer allowed. New work is required to follow new rules, so you only need to replace it when it is otherwise necessary in the course of remodeling, maintenance, etc.
I've been rewiring my old house for about 6 months now (off and on), and I run 12G wire on 15A circuits and add a 14G bonding wire if I have any concern about the mechanical connection. Is this the same issue?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!