Black 12 awg
white 12 awg
ground 14 awg
14 gauge ground wire
The installers evidently forgot that although they were doing more than required, they must still comply with all the rules, in this case, the equipment ground must be #12.( presuming that the #12 wire is connected to a 20 amp breaker, if it is connected to a 15 amp breaker, all is well).
There is some danger to this installation, but I can think of a lot of other things that are more hazardous. However, it is always best to be in complete compliance with the NEC, so I'd advise having this problem corrected.
This practice is no longer allowed. New work is required to follow new rules, so you only need to replace it when it is otherwise necessary in the course of remodeling, maintenance, etc.
I've been rewiring my old house for about 6 months now (off and on), and I run 12G wire on 15A circuits and add a 14G bonding wire if I have any concern about the mechanical connection. Is this the same issue?
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING