(A) Combustible Material. Luminaires (fixtures) shall be installed so that adjacent combustible material will not be subjected to temperatures in excess of 90¬∞C (194¬∞F).
(B) Fire-Resistant Construction. Where a luminaire (fixture) is recessed in fire-resistant material in a building of fire-resistant construction, a temperature higher than 90¬∞C (194¬∞F) but not higher than 150¬∞C (302¬∞F) shall be considered acceptable if the luminaire (fixture) is plainly marked that it is listed for that service.
(C) Recessed Incandescent Luminaires (Fixtures).
Incandescent luminaires (fixtures) shall have thermal protection and shall be identified as thermally protected.
Because many recessed incandescent luminaires are suitable for a wide variety of lamp sizes and types and finish trims, the temperature close to the lamp can vary widely.
Therefore, many manufacturers have chosen to locate thermal protectors away from the source of heat, such as in the outlet box, and to design the protector so that it will detect a change in temperature resulting from the addition of thermal insulation around the luminaire.
This design prevents nuisance tripping of the protector (as a result of changing lamp wattage, for example) but still provides protection against overheating arising from thermal insulation around a recessed luminaire not designed for such use.
Exception No. 1: Thermal protection shall not be required in a recessed luminaire (fixture) identified for use and installed in poured concrete.
Exception No. 2: Thermal protection shall not be required in a recessed luminaire (fixture) whose design, construction, and thermal performance characteristics are equivalent to a thermally protected luminaire (fixture) and are identified as inherently protected.
Recessed incandescent luminaires without thermal protection are not permitted unless they are listed and identified as providing equivalent temperature protection by construction design.
Thermal protection is provided to deactivate the lamp should the luminaire be mislamped so that it overheats.
410.66 Clearance and Installation.
(1) Non-Type IC. A recessed luminaire (fixture) that is not identified for contact with insulation shall have all recessed parts spaced not less than 13 mm (¬Ω in.) from combustible materials.
The points of support and the trim finishing off the opening in the ceiling or wall surface shall be permitted to be in contact with combustible materials.
(2) Type IC.
A recessed luminaire (fixture) that is identified for contact with insulation, Type IC, shall be permitted to be in contact with combustible materials at recessed parts, points of support, and portions passing through or finishing off the opening in the building structure.
(B) Installation. Thermal insulation shall not be installed above a recessed luminaire (fixture) or within 75 mm (3 in.) of the recessed luminaire‚Äôs (fixture‚Äôs) enclosure, wiring compartment, or ballast unless it is identified for contact with insulation, Type IC.
(A) General. Conductors that have insulation suitable for the temperature encountered shall be used.
(B) Circuit Conductors.
Branch-circuit conductors that have an insulation suitable for the temperature encountered shall be permitted to terminate in the luminaire (fixture).
(C) Tap Conductors.
Tap conductors of a type suitable for the temperature encountered shall be permitted to run from the luminaire (fixture) terminal connection to an outlet box placed at least 300 mm (1 ft) from the luminaire (fixture).
Such tap conductors shall be in suitable raceway or Type AC or MC cable of at least 450 mm (18 in.) but not more than 1.8 m (6 ft) in length.
Quality recessed lighting????
Dimmer switches and recessed lights
Recessed lights for first floor kitchen..precautions?
Junction Box question for recessed lights
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 25 Insanely Easy-to-Make Holiday Ornaments
- 20 Easy 60-Minute Home Improvements
- 10 Classic Ways to Brighten Up a Dark Room
- 10 Quick and Creative Stocking Stuffers
- 133 Smart Storage Ideas for the Whole House
- 7 Unauthorized Uses for Common Appliances
- 8 Ways to Make a Small Room Look Big
- Best Secret Hiding Spots We've Ever Seen
- Sweet Dreams: 15 Inventive Beds You Can Make Yourself
- 11 Ways to Winterize Your Home
- Laundry Room Ideas to Knock Your Socks Off
- 10 Must-Do Projects for November
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 10 Houseplants You Can Grow ANYWHERE
- 10 Doable Designs for a DIY Rug
- 7 Incredible Uses for Salvaged Lumber
- 10 Bookcases You Can Make Yourself
- 7 Mistakes Not to Make with Your Fireplace
- The Easy 1-Hour Money-Saving Home Checkup
- Quick Fixes for a Fresher Shower
- Don't Try This at Home: 7 Dangerous DIYs
- 10 Ways to Redecorate Without Spending a Dime
- The Top 10 Artificial Christmas Trees