tripping breaker help!!!!!!
If it is wired with #12 wire, you could go to a 20-amp breaker, but no bigger.
I would ABSOLUTELY NOT put in a bigger breaker, unless there's some way to be SURE that (as rpxlpx says) #12 wiring makes up that entire circuit. (Not easy to determine.) #14 wire is pretty thin stuff--you don't want to take chances.
Better to, if possible, run a new circuit to help alleviate the problem.
[This message has been edited by k2 (edited January 22, 2004).]
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING