I just experienced a melted connection nut on my new furnace where the neutral neutral wire from the circut box connects to the furnace. It requires a 15 amp circuit breaker.
One single seperate circuit wire to the furnace, 14 ga sheathed electrical cable with ground.It did not throw the breaker, just melted and shut down the furnace.
I cleaned it up and reconnected and it is working ok but I am still wondering if it is safe?? Checked wire back to breaker, nothing unusual.
Any suggestions as to why and safety in the future.Chuck
It sounds like the wirenut was loose and therefore you had some arcing in the connection. Is the lead from the furnace a stranded conductor? A stranded conductor should be stripped longer and wrapped around the solid conductor and then wirenutted. What size/color wirenut was it? What brand?
I need some Pergo Causual living Summerview Oak / Ch...
POWR-KRAFT wood lathe
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 21 Ways to Spring Clean—Naturally
- Show Off: 9 Ways to Display a Collection
- The Best Paint Colors for Low-Light Rooms
- 7 Easy Budget-Friendly Backyard Makeovers
- 8 Clever Storage Solutions for Pots & Pans
- 8 Creative OTHER Ways to Use a Closet
- 12 Tiny Gardens to Grow on a Tabletop
- 15 Eye-Catching Front Door Options
- 12 Places You Never Clean—But Should!