I just experienced a melted connection nut on my new furnace where the neutral neutral wire from the circut box connects to the furnace. It requires a 15 amp circuit breaker.
One single seperate circuit wire to the furnace, 14 ga sheathed electrical cable with ground.It did not throw the breaker, just melted and shut down the furnace.
I cleaned it up and reconnected and it is working ok but I am still wondering if it is safe?? Checked wire back to breaker, nothing unusual.
Any suggestions as to why and safety in the future.Chuck
It sounds like the wirenut was loose and therefore you had some arcing in the connection. Is the lead from the furnace a stranded conductor? A stranded conductor should be stripped longer and wrapped around the solid conductor and then wirenutted. What size/color wirenut was it? What brand?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- Make Your Bed: 9 DIY Headboards
- Insanely Easy 60-Minute Home Improvements
- Space-Saving Solutions for Tiny Bedrooms
- 9 Perfect Color Combos for Your Home
- 22 Tiny Houses We Love
- See the Most Highly Anticipated Colors for 2015
- What's the Best Color for Living Rooms?
- Favorite Space-Saving Double-Duty Furniture
- 10 Low-Cost DIY Home Security Solutions
- Redecorate Without Spending a Dime: 10 Ideas
- 10 Houseplants You Can Grow Anywhere
- 9 Amazing Mobile Home Makeovers
- 10 Doable Designs for a DIY Rug
- 9 Alternative Uses for Toothpaste
- Live Large in a (Very) Small Space
- 8 Cheap and Unique DIY Nightstands
- 15 Eye-Catching Options for Your Front Door
- Supersize Your Small Bath with 8 Pro Tips
- Don't Try This at Home: 7 Dangerous DIYs
- 10 Simple Woodworking Projects
- Is There Anything Vinegar Can't Do?
- 7 Incredible Uses for Salvaged Lumber
- 12 Tiny Gardens You Can Grow on a Tabletop
- 16 Sneaky Storage Ideas
- 10 Surprisingly Smart Solutions for Junk Drawers
- Bright & Bold Colors for Your Front Door
- DIY Bookcases: 16 Easy Project Ideas
- Don't Make These 7 Fireplace Mistakes