Hi all! Here's my trouble: On Cir #7, I have 4 standard 120v duplex outlets. When tested with the circuit analyzer, they are registering "OPEN GROUND". When we pulled one outlet out of the wall, blk&white wires were screwed down and the ground wire was as well (2-wire cable w/ground). Why do they register "OPEN GROUND" when tested? Could one outlet on that circuit NOT be grounded at all? What is the best way to fix the problem?
You have an open ground wire somewhere on the circuit. It could even be in the main panel. Is the entire circuit wired with 2 wire + ground cable? Sometimes people add on to existing circuits that don't have a ground.
More info: after further testing, we have found that 2 of the 4 duplex outlets do in fact APPEAR to have black,white and grd; all secured. The end does NOT have a grd same holds true for the first. Is there a method to ADD a ground to #1 and #4? I alos note #1 and #4 are in plastic boxes, not metal.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!