Hi all! Here's my trouble: On Cir #7, I have 4 standard 120v duplex outlets. When tested with the circuit analyzer, they are registering "OPEN GROUND". When we pulled one outlet out of the wall, blk&white wires were screwed down and the ground wire was as well (2-wire cable w/ground). Why do they register "OPEN GROUND" when tested? Could one outlet on that circuit NOT be grounded at all? What is the best way to fix the problem?
You have an open ground wire somewhere on the circuit. It could even be in the main panel. Is the entire circuit wired with 2 wire + ground cable? Sometimes people add on to existing circuits that don't have a ground.
More info: after further testing, we have found that 2 of the 4 duplex outlets do in fact APPEAR to have black,white and grd; all secured. The end does NOT have a grd same holds true for the first. Is there a method to ADD a ground to #1 and #4? I alos note #1 and #4 are in plastic boxes, not metal.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love