I just ran a new outlet to a bathroom yesterday. It's a single outlet on a GFCI circuit-breaker. It's the only thing on that breaker. Two years ago an electrician put in a kitchen outlet for me, which is also a single outlet on a single breaker (oddly, he didn't use GFCI).
It just now occurred to me that I could save a slot in my breaker box if I hung both these outlets off that new GFCI breaker that I put in yesterday. Plus, I'd get ground-faulting in the kitchen. The way the wiring's been done, this would be a trivial change to make. Does the NEC allow a 20-amp GFCI breaker to serve one outlet in a bathroom and one other outlet in a kitchen?
Well, I managed to grab a look at the NEC over lunch, and it's pretty clear that the answer to my question is "no". That's too bad. I hate to waste two panel slots for just two outlets, but I guess that's just what you have to live with when you add outlets in a onesy-twosy fashion.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- 15 Fast Fixes for Your Home Facade
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers