I just ran a new outlet to a bathroom yesterday. It's a single outlet on a GFCI circuit-breaker. It's the only thing on that breaker. Two years ago an electrician put in a kitchen outlet for me, which is also a single outlet on a single breaker (oddly, he didn't use GFCI).
It just now occurred to me that I could save a slot in my breaker box if I hung both these outlets off that new GFCI breaker that I put in yesterday. Plus, I'd get ground-faulting in the kitchen. The way the wiring's been done, this would be a trivial change to make. Does the NEC allow a 20-amp GFCI breaker to serve one outlet in a bathroom and one other outlet in a kitchen?
Well, I managed to grab a look at the NEC over lunch, and it's pretty clear that the answer to my question is "no". That's too bad. I hate to waste two panel slots for just two outlets, but I guess that's just what you have to live with when you add outlets in a onesy-twosy fashion.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING