I just ran a new outlet to a bathroom yesterday. It's a single outlet on a GFCI circuit-breaker. It's the only thing on that breaker. Two years ago an electrician put in a kitchen outlet for me, which is also a single outlet on a single breaker (oddly, he didn't use GFCI).
It just now occurred to me that I could save a slot in my breaker box if I hung both these outlets off that new GFCI breaker that I put in yesterday. Plus, I'd get ground-faulting in the kitchen. The way the wiring's been done, this would be a trivial change to make. Does the NEC allow a 20-amp GFCI breaker to serve one outlet in a bathroom and one other outlet in a kitchen?
Well, I managed to grab a look at the NEC over lunch, and it's pretty clear that the answer to my question is "no". That's too bad. I hate to waste two panel slots for just two outlets, but I guess that's just what you have to live with when you add outlets in a onesy-twosy fashion.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- 142 Remarkable Houses Around the World
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers
- 159 Smart Storage Ideas for the Whole House
- 10 Room Dividers to Bring Order to Your Space
- Shelf Life: 10 Bookcase Projects You Can DIY
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- 11 Amazing Homemade Sheds to Inspire Your Own
- Secret Rooms: 10 Special Spaces Hidden from Sight
- 17 Design Inspirations for Mudrooms and Entryways
- Recipe for Success: 10 Easy Kitchen Storage Hacks
- Winning Combinations: 9 "Can't Miss" Color Schemes
- Laundry Room Ideas to Knock Your Socks Off
- The Ultimate All-Natural Cleaning Guide