I currently have a box with an empty switch - the top goes to a ceiling fan on the back porch and I hooked the bottom (empty) to a flood light - the problem is when I turn on one - they both come on. Also in the box is a dimmer switch.
The way it's wired: all white wires are connected - the black from the breaker goes to one screw on the top switch (fan) then into a pigtail split to the black for the dimmer and to the bottom switch (flood). The black wire from the fan and flood are on the respective switch - opposite the black from the breaker.
What's wrong with this setup - is it possible for the wiring to be right and the switch to have some sort of jummper?? that would allow current to the fan when the flood switch is on - even with the fan switch off? Please Help!! Thanks in advance!
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries