I currently have a box with an empty switch - the top goes to a ceiling fan on the back porch and I hooked the bottom (empty) to a flood light - the problem is when I turn on one - they both come on. Also in the box is a dimmer switch.
The way it's wired: all white wires are connected - the black from the breaker goes to one screw on the top switch (fan) then into a pigtail split to the black for the dimmer and to the bottom switch (flood). The black wire from the fan and flood are on the respective switch - opposite the black from the breaker.
What's wrong with this setup - is it possible for the wiring to be right and the switch to have some sort of jummper?? that would allow current to the fan when the flood switch is on - even with the fan switch off? Please Help!! Thanks in advance!
It sounds like you have a duplex switch. The line side is hooked up the the load side and vice versa, reverse the feed and loads, and see what happens.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Picture-Perfect Patios: 10 Outdoor Spaces to Love
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers