I currently have a box with an empty switch - the top goes to a ceiling fan on the back porch and I hooked the bottom (empty) to a flood light - the problem is when I turn on one - they both come on. Also in the box is a dimmer switch.
The way it's wired: all white wires are connected - the black from the breaker goes to one screw on the top switch (fan) then into a pigtail split to the black for the dimmer and to the bottom switch (flood). The black wire from the fan and flood are on the respective switch - opposite the black from the breaker.
What's wrong with this setup - is it possible for the wiring to be right and the switch to have some sort of jummper?? that would allow current to the fan when the flood switch is on - even with the fan switch off? Please Help!! Thanks in advance!
It sounds like you have a duplex switch. The line side is hooked up the the load side and vice versa, reverse the feed and loads, and see what happens.
Rewiring bathroom, need to remove a switch!!!!
Adding A Light Switch
Challenging electrical problem
Wiring a switch/receptacle combo on an end run - help!
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects