I currently have a box with an empty switch - the top goes to a ceiling fan on the back porch and I hooked the bottom (empty) to a flood light - the problem is when I turn on one - they both come on. Also in the box is a dimmer switch.
The way it's wired: all white wires are connected - the black from the breaker goes to one screw on the top switch (fan) then into a pigtail split to the black for the dimmer and to the bottom switch (flood). The black wire from the fan and flood are on the respective switch - opposite the black from the breaker.
What's wrong with this setup - is it possible for the wiring to be right and the switch to have some sort of jummper?? that would allow current to the fan when the flood switch is on - even with the fan switch off? Please Help!! Thanks in advance!
It sounds like you have a duplex switch. The line side is hooked up the the load side and vice versa, reverse the feed and loads, and see what happens.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love