Recently, I popped in a GFCI breaker to protect a kitchen-counter outlet that until now has not been GFCI protected. That outlet is the only outlet on the breaker. The white wire from the breaker is stranded. Is it ok to stick that stranded wire in the neutral bus with all the other neutral wires? Is it ok to screw down a stranded wire?
As long as the screw is rated for the wire it is ok to screw the stranded wire. Usually the new panels are the compression type which will be fine. If it is on an older panel with a threaded screw into a neutral bar, then you would have to use a lug on the end.
My neutral bar has threaded screws. You stick the wire straight into a slot, tighten the screw down, and the screw compresses the wire into the slot.
disconnected neutral wire
GFCI Receptacle or GFCI Breaker?
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!