Recently, I popped in a GFCI breaker to protect a kitchen-counter outlet that until now has not been GFCI protected. That outlet is the only outlet on the breaker. The white wire from the breaker is stranded. Is it ok to stick that stranded wire in the neutral bus with all the other neutral wires? Is it ok to screw down a stranded wire?
As long as the screw is rated for the wire it is ok to screw the stranded wire. Usually the new panels are the compression type which will be fine. If it is on an older panel with a threaded screw into a neutral bar, then you would have to use a lug on the end.
My neutral bar has threaded screws. You stick the wire straight into a slot, tighten the screw down, and the screw compresses the wire into the slot.
disconnected neutral wire
GFCI Receptacle or GFCI Breaker?
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects