Recently, I popped in a GFCI breaker to protect a kitchen-counter outlet that until now has not been GFCI protected. That outlet is the only outlet on the breaker. The white wire from the breaker is stranded. Is it ok to stick that stranded wire in the neutral bus with all the other neutral wires? Is it ok to screw down a stranded wire?
As long as the screw is rated for the wire it is ok to screw the stranded wire. Usually the new panels are the compression type which will be fine. If it is on an older panel with a threaded screw into a neutral bar, then you would have to use a lug on the end.
My neutral bar has threaded screws. You stick the wire straight into a slot, tighten the screw down, and the screw compresses the wire into the slot.
disconnected neutral wire
GFCI Receptacle or GFCI Breaker?
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 25 Clever Ideas for Repurposed Storage
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 30 Things Every Homeowner Should Know How to Do
- 11 Clever Alternatives to Kitchen Cabinets
- 159 Storage Ideas for Space-Starved DIYers
- 21 "Expert Picks" for Fail-Safe Colors
- 9 Easy Ways to Kill Weeds Effectively
- 20 Ways to Make a Small Bathroom Big
- Simple “Under $60” Curb Appeal Updates for Any Home
- 67 Expert Tips to Aid Your Spring Cleaning
- 10 Eye-Catching Options for Your Front Door
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight