Recently, I popped in a GFCI breaker to protect a kitchen-counter outlet that until now has not been GFCI protected. That outlet is the only outlet on the breaker. The white wire from the breaker is stranded. Is it ok to stick that stranded wire in the neutral bus with all the other neutral wires? Is it ok to screw down a stranded wire?
As long as the screw is rated for the wire it is ok to screw the stranded wire. Usually the new panels are the compression type which will be fine. If it is on an older panel with a threaded screw into a neutral bar, then you would have to use a lug on the end.
My neutral bar has threaded screws. You stick the wire straight into a slot, tighten the screw down, and the screw compresses the wire into the slot.
disconnected neutral wire
GFCI Receptacle or GFCI Breaker?
Installing a 50 Amp GFCI breaker for use with Hot tub.
- 10 Old House Features We Were Wrong to Abandon
- 11 Tiny Bathrooms We Love
- 12 Insanely Easy 60-Minute Home Improvements
- Kitchen Envy: 10 Rooms We Love
- 25 Clever Ideas for Repurposed Storage
- 10 Surprising Ways to Cure Household Odors
- 11 Ways to Winterize Your Home on a Budget
- 10 Ways to Live Large in a Small Space
- 10 Eye-Catching Options for Your Front Door
- Dressing Up the Dresser: 11 Clever DIY Transformations
- 12 Hobbit Houses to Make You Consider Moving Underground
- 10 Ways to Use Mirrors to Your Design Advantage
- 10 New Uses for Old Doors
- How To: Paint EVERYTHING
- Man, Oh Man! 7 Unbelievable Guy Spaces
- Assembly Required: 15 DIY Kit Homes
- 12 Wow-Worthy Woods for Kitchen Countertops
- 10 "Neat" Garage Storage Solutions
- 10 Houseplants to Improve Indoor Air Quality
- How To: Clean EVERYTHING