I'm changing 2 prong outlets to 3 prong. The house was built in 1957. The boxes are grounded as there is the bare wire coming into the box and wraping around the screw in the back.
Whats the best way to ground the new receptables? a self grounding receptable or a wire from the green screw on the receptable to the screw in the back of the box (where the grounding is attached)?
As long as the ground wire is attached to the box, the box is metal, the mounting screws go directly to the box, the metal of the receptacle will touch the box when screwed tight ,then you should be good. If there is a gap and you have to shim the receptacle, then you will need additional ground conection. There are specification grade receptacles which have a ground spring at the mounting screw. You can also use the ground jumper to the back of the box, but only one wire on the screw, so you may have to pigtail.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Picture-Perfect Patios: 10 Outdoor Spaces to Love
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers