I am going to run a sub panel to my detached garage undergrond in plastic conduit. It will be a 50 amp subpanel, I was told I could use alum wire (6 ga) seems ok since the feed coming into the house is also alum. I thought it was unsafe to run alum cable? Or was that just back in the day. It sure is cheaper than copper.
You can use Aluminum. It is usually used for services and feeders, but not on branch circuits. Dont nick the wire when you skin it, Use a wire brush to shine it a bit. use penetrox to prevent oxidation. Wiggle the wire near the screw when tightening . Tighten it a couple of times, it tends to loosen a bit. Make sure your lugs are rated for aluminum and never let share in the same connection with a copper conductor. They must be separated.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 11 Lessons to Learn from AirBnB's Tiniest Homes
- 10 DIY Ways to Redo Your Wall—Without Paint
- 8 Smart Shoe Racks You Can Make Today
- 7 Easy Budget-Friendly Backyard Makeovers
- Worth It: 8 Renovations That Pay You Back
- 7 House Sounds Never to Ignore
- Watch These 10 Home Trends Take Off in 2015
- 11 Things Never to Keep in Your Bedroom
- 12 Places You Never Clean—But Should!