I am going to run a sub panel to my detached garage undergrond in plastic conduit. It will be a 50 amp subpanel, I was told I could use alum wire (6 ga) seems ok since the feed coming into the house is also alum. I thought it was unsafe to run alum cable? Or was that just back in the day. It sure is cheaper than copper.
You can use Aluminum. It is usually used for services and feeders, but not on branch circuits. Dont nick the wire when you skin it, Use a wire brush to shine it a bit. use penetrox to prevent oxidation. Wiggle the wire near the screw when tightening . Tighten it a couple of times, it tends to loosen a bit. Make sure your lugs are rated for aluminum and never let share in the same connection with a copper conductor. They must be separated.
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 17 Design Inspirations for Mudrooms and Entryways
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Laundry Room Ideas to Knock Your Socks Off
- 10 Unexpected Spots for Accent Colors
- 11 Clever Alternatives to Kitchen Cabinets
- 159 Smart Storage Ideas for the Whole House
- 21 "Expert Picks" for Fail-Safe Colors
- 9 Easy Ways to Kill Weeds Effectively
- 20 Ways to Make a Small Bathroom Big
- 7 Easy Budget-Friendly Backyard Makeovers
- 11 Homemade Sheds to Fill Your Storage Needs
- Ultimate Lawn Care Guide: 12 Steps to a Prize-Winning Yard
- 10 Room Dividers to Bring Order to Your Space
- 11 Creative Garden Borders You Can Make—Easily!
- Tips and Tricks to Fit More into Less Closet Space
- Secret Rooms: 10 Special Spaces Hidden from Sight