I am going to run a sub panel to my detached garage undergrond in plastic conduit. It will be a 50 amp subpanel, I was told I could use alum wire (6 ga) seems ok since the feed coming into the house is also alum. I thought it was unsafe to run alum cable? Or was that just back in the day. It sure is cheaper than copper.
You can use Aluminum. It is usually used for services and feeders, but not on branch circuits. Dont nick the wire when you skin it, Use a wire brush to shine it a bit. use penetrox to prevent oxidation. Wiggle the wire near the screw when tightening . Tighten it a couple of times, it tends to loosen a bit. Make sure your lugs are rated for aluminum and never let share in the same connection with a copper conductor. They must be separated.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 16 Sneaky Storage Ideas
- 20 Easy 60-Minute Home Improvements
- 9 Ways to Troubleshoot the Furnace
- 11 Real Haunted Houses to Visit--If You Dare!
- 9 Alternative Uses for Toothpaste
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 8 Ways to Make a Small Room Look Big
- 21 Expert Picks for Fail-Safe Colors
- 10 Fall Door DIYs for the Best House on the Block
- The Cheapest Ways to Boost Home Value
- 10 New Uses for Old Doors
- 10 Unexpected Uses for Spray Paint
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 8 Amazing Handmade Kitchen Counters
- 10 New Uses for Old Dressers
- 7 Upgrades You Can Do in Under 300 Seconds
- 10 Thrifty DIY Ways to Organize Your Home
- 26 Easy Painted Pumpkins for Halloween
- 9 Totally Amazing Mobile Home Makeovers
- 5 "Make in a Weekend" Bookshelf Projects
- 9 Decorating Lessons We Learned from Social Media
- 10 "Zero Dollar" Storage Hacks
- 121 DIY Ideas for Halloween
- The 10 Best Things to Buy Secondhand
- 16 Must-See Coffee Tables You Can DIY—Easily!