Help. My mother and I rewired a mess of wires under the ceiling fan to fix an outlet and outside light that did not have any power. The outlet works fine, but the light is a mess. When we turn the circuit breaker on, the light comes on, but when we try to turn the light off at the switch the circuit breaker trips.
It sounds like you have wired it so that when the switch is supposed be turning off the light it is actually turning on the switch and the wiring is such that it is shorting out the 115V from the panel. It is common to run a single cable from a light fixture to the switch and wire it so that one lead is the "hot" lead and the other is the switched lead back from the switch. (The "white" lead from the switch is not really a neutral wire but a switched hot lead. When I wire a switch this way I always color code the white wire with colored tape. no questions about it being a neutral then.) You need to trce out where all the wires go from the box that you did the rewiring in and then see if you can do what you want.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!