Hello, I have a room which has only a light fixture and a switch to turn this light fixture on/off - there is nothing else. I would like to put a freezer in there so I purchased a switch/receptacle combo unit to replace the switch with the goal of having the switch operate the light fixture and the receptacle always on for the freezer. The switch is (I think) at the end of a run so in the box there is a black/hot, a white/neutral, and a bare/ground. There are no other wires in the box.
The instructions for the cooper combo device (274/3274) were to wire black to the black screw nearest the switch and leave a tab intact that runs between the first black screw near the switch and a second black screw nearest the receptacle on the left side. Then to wire ground to the green screw in the middle on the right side. The neutral was to be run to the copper screw nearest the switch AND to the silver screw nearest the receptacle I - I used a wire nut to connect two short wires to the neutral and ran the first to the copper and the second to the silver screws.
When I returned power I noticed that when the light is on, my receptacle has no power. When the light is off then power returns to the receptacle for the freezer.
Can anyone offer ideas on how to resolve this? It's driving me nuts! :-D
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries