Here is my problem, if anyone can help that would be great!!
first of all I am using a 40 amp breaker to feed the disconnect, do i need to use 8awg wire or will 10 be sufficient? next... since it's a 220 hook up i'm confused as to what to do with the white(neutral wire) the box i purchased is labeled as a central air disconnect. it has 2 line terminals 2 load terminals and a grounding block. it also has a gfci outlet in it. I hope this enough info to get an answer, it's getting warm here and my wife is getting impatient with me!!
Get Help from Bob Vila
- Give-Aways & Offers
- Monthly Must Do's
- DIY Project Ideas
- Step-by-Step Guides
- Inspirational Photo Galleries