I'm replacing our kitchen countertop 20-amp small appliance outlet with a GFCI outlet. This outlet is the only item this circuit.
I removed the old outlet to find only two wires, the red hot wire and the white return wire. The box is metal, connected by flexible armored cable and metal conduit to the service panel (so I assume that connection is the only ground).
But ... there's no grounding terminal in the outlet box for me to wire the GFCI's green grounding terminal to.
The GFCI installation instructions do not state whether it is necessary for the receptacle's grounding terminal to be attached to 'something' for it to function properly.
Should I 'create' a grouding terminal in the box myself by driving a screw into one of the small holes in the back of the box?
Or will screwing the GFCI to the box create a sufficient ground connection?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- See the Most Highly Anticipated Colors for 2015
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 10 Unexpected Spots for Accent Colors
- 10 Fantastic Furniture Makeovers
- Worth It: 8 Renovations That Pay You Back
- 9 Closet Storage Tips from a Pro Organizer
- 7 Seriously Surprising Spots for a Fireplace
- Laundry Room Ideas to Knock Your Socks Off
- 12 Tiny Gardens to Grow on a Tabletop
- Supersize Your Small Bathroom with 8 Tips
- Kitchen Envy: 10 Rooms We Love