I'm replacing our kitchen countertop 20-amp small appliance outlet with a GFCI outlet. This outlet is the only item this circuit.
I removed the old outlet to find only two wires, the red hot wire and the white return wire. The box is metal, connected by flexible armored cable and metal conduit to the service panel (so I assume that connection is the only ground).
But ... there's no grounding terminal in the outlet box for me to wire the GFCI's green grounding terminal to.
The GFCI installation instructions do not state whether it is necessary for the receptacle's grounding terminal to be attached to 'something' for it to function properly.
Should I 'create' a grouding terminal in the box myself by driving a screw into one of the small holes in the back of the box?
Or will screwing the GFCI to the box create a sufficient ground connection?
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects