I'm replacing our kitchen countertop 20-amp small appliance outlet with a GFCI outlet. This outlet is the only item this circuit.
I removed the old outlet to find only two wires, the red hot wire and the white return wire. The box is metal, connected by flexible armored cable and metal conduit to the service panel (so I assume that connection is the only ground).
But ... there's no grounding terminal in the outlet box for me to wire the GFCI's green grounding terminal to.
The GFCI installation instructions do not state whether it is necessary for the receptacle's grounding terminal to be attached to 'something' for it to function properly.
Should I 'create' a grouding terminal in the box myself by driving a screw into one of the small holes in the back of the box?
Or will screwing the GFCI to the box create a sufficient ground connection?
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!