one question here.
installing a 100 amp lug subpanel in my basement to be feed from 100 amp breaker in main panel...
what type/size of wire am i asking for ?
You may use #4 copper (two hot, one neutral) and a #8 copper ground (insulated), type THHN or THWN in most jurisdictions.
If your work will be subject to inspection, many jurisdictions rigorously enforce the ampacity tables and the exception that allows #4 copper for dwelling services or "the main feeder" would not be allowed for a sub-panel. #3 THHN copper would be the minimum size and if you will be using a cable such as NM-B, #2 copper would be the required size. If in doubt, consult your local inspector.
Installing a subpanel in the basement
Installing Subpanel and Florescent Lighting Questions
recommended wire size for 100 amp service
- 15 Old House Features We Were Wrong to Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 70 Gardening Tricks and Ideas for Total Beginners
- 16 Inventive Beds You Can Make Yourself
- Top 10 Classic DIY Projects for the Outdoors
- 15 Once-Popular Household Items That Are Vanishing
- 159 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 10 Wise Ways to Get Rid of Pests and Critters
- Before and After: 9 Totally Amazing Mobile Home Makeovers
- Top Tips for Keeping Countertops Like New
- 15 Amazing Things You Can Make with $0 Scrap Wood
- 14 Ways to Get More Kitchen Counter Space
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in 1 Day
- 9 Tried-and-True Methods of Eliminating Weeds
- Picture-Perfect Patios: 10 Outdoor Spaces to Love
- 11 Clever Alternatives to Kitchen Cabinets
- 7 Easy Budget-Friendly Backyard Makeovers