one question here.
installing a 100 amp lug subpanel in my basement to be feed from 100 amp breaker in main panel...
what type/size of wire am i asking for ?
You may use #4 copper (two hot, one neutral) and a #8 copper ground (insulated), type THHN or THWN in most jurisdictions.
If your work will be subject to inspection, many jurisdictions rigorously enforce the ampacity tables and the exception that allows #4 copper for dwelling services or "the main feeder" would not be allowed for a sub-panel. #3 THHN copper would be the minimum size and if you will be using a cable such as NM-B, #2 copper would be the required size. If in doubt, consult your local inspector.
Installing a subpanel in the basement
Installing Subpanel and Florescent Lighting Questions
recommended wire size for 100 amp service
100 amp sub panel
- 15 Old House Features We Shouldn't Abandon
- 13 Lazy Cleaning Tricks for a Spotless Home
- Laundry Room Ideas to Knock Your Socks Off
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 7 House Sounds You Never Want to Ignore
- 10 Surprisingly Simple Woodworking Projects
- Worth It: 8 Renovations That Pay You Back
- Organize Your Life with 12 Dollar-Store Buys
- 9 Totally Amazing Mobile Home Makeovers
- Don't Make These 7 Mistakes in Small Spaces
- 20 Sneaky Storage Ideas
- 15 Totally Unexpected DIY Flooring Alternatives
- 7 Easy Budget-Friendly Backyard Makeovers
- 10 Closet Cures That Cost Less Than $100
- 11 Easy DIY Projects to Declutter Your Home
- 10 "Zero Dollar" Garden Hacks
- 10 Killproof Plants for a No-Effort Landscape
- 9 Insanely Easy 1-Hour Backyard Projects