one question here.
installing a 100 amp lug subpanel in my basement to be feed from 100 amp breaker in main panel...
what type/size of wire am i asking for ?
You may use #4 copper (two hot, one neutral) and a #8 copper ground (insulated), type THHN or THWN in most jurisdictions.
If your work will be subject to inspection, many jurisdictions rigorously enforce the ampacity tables and the exception that allows #4 copper for dwelling services or "the main feeder" would not be allowed for a sub-panel. #3 THHN copper would be the minimum size and if you will be using a cable such as NM-B, #2 copper would be the required size. If in doubt, consult your local inspector.
Installing a subpanel in the basement
Installing Subpanel and Florescent Lighting Questions
recommended wire size for 100 amp service
100 amp sub panel
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 20 Insanely Easy 60-Minute Home Improvements
- 9 Expert Furniture Arranging Tips
- 16 Inventive Beds You Can Make Yourself
- World's Most Amazing Slip 'N Slide
- 13 Lanterns For Your Porch, Patio, or Garden
- 133 Smart Storage Ideas for the Whole House
- 30 Things Every Adult Should Know How to Do
- 16 New Ways to Store Kitchen Necessities
- 12 Garden Sheds You Could Live (or Work) In
- 11 Big Ideas for Small Kitchens
- 47 Industrial Kitchens
- 283 Great DIY Project Ideas
- The Right Path: 15 Wonderful Walkway Designs
- Laundry Room Ideas to Knock Your Socks Off
- 17 Backsplashes for a Unique Kitchen
- Assembly Required: 15 DIY Kit Homes
- 18 Bathroom Updates You Can Do in a Day
- Easy DIY Fixes for 11 Annoying House Problems
- Capitalize on Your Attic: 10 Inspirations
- 14 Room Dividers to Organize Your Space
- 10 Creative New Ways to Use Old Bottles
- Make Good Use of Old Junk: 14 Creative Ideas
- 22 Tiny Houses We Love
- 10 Smart Solutions for Small Bedrooms
- 5 DIY Porch Swings Perfect for Summer
- 1 Dozen Ways to Maximize a Small Yard
- 20 Ways to Make a Small Bathroom Big
- 5 Easy and Creative DIY Lamps