one question here.
installing a 100 amp lug subpanel in my basement to be feed from 100 amp breaker in main panel...
what type/size of wire am i asking for ?
You may use #4 copper (two hot, one neutral) and a #8 copper ground (insulated), type THHN or THWN in most jurisdictions.
If your work will be subject to inspection, many jurisdictions rigorously enforce the ampacity tables and the exception that allows #4 copper for dwelling services or "the main feeder" would not be allowed for a sub-panel. #3 THHN copper would be the minimum size and if you will be using a cable such as NM-B, #2 copper would be the required size. If in doubt, consult your local inspector.
Installing a subpanel in the basement
Installing Subpanel and Florescent Lighting Questions
recommended wire size for 100 amp service
100 amp sub panel
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 15 Fast Facade Fixes for Instant Curb Appeal
- 9 Expert Furniture Arranging Tips
- 16 Inventive Beds You Can Make Yourself
- 13 Lanterns For Your Porch, Patio, or Garden
- 5 Ways to Repurpose Old Window Screens
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 7 Smart Shoe Racks You Can Make Today
- 12 Garden Sheds You Could Live (or Work) In
- Clearing the Air: 10 Natural Ways to Remedy Household Odors
- 12 Hobbit Houses to Make You Consider Moving Underground
- 16 Cool DIY Coffee Tables
- 10 Fall Home Maintenance Musts
- Supersize Your Small Bath With These 8 Pro Tips
- 15 Neat Garage Storage Solutions
- Buy or Build: 15 Desks We Love
- 10 Great DIY Bookshelf Projects
- 5 Minutes Flat: 7 Upgrades You Can Do in Under 300 Seconds
- 10 Creative New Ways to Use Old Bottles
- 10 FREE Storage Hacks
- 10 New Uses for Old Doors
- 10 "Must Do" September Projects
- 9 Calming Colors for a Serene Home
- 16 Easy Ideas for Customized Cabinets
- 17 Mini Bars to Mix Up Your Home Decor
- 20 Ways to Make a Small Bathroom Big
- 12 Unique DIY Kitchen Island Designs