I have a hot tub that has only connections for 2 hots and a ground. My 50 amp sub panel has a gfci breaker with the hard wired neutral connected to the neutral bus bar in the sub panel. The GFCI itself has places for 2 load hots and 1 load neutral. Since the hot tub has no neutral point of connection, can I ignore the neutral completely?
As long as the white pigtail from the breaker is connected to the neutral bar in the subpanel, this will work with only the two hots connected to the breaker.
tracing underground landscape light wiring
BUILDING WOODEN BOX TO COVER UP SOME ELECTRICAL STUFF!!
replace lamp post and wiring
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 30 Things Everyone Should Know
- 16 Sneaky Storage Ideas
- 20 Easy 60-Minute Home Improvements
- 9 Ways to Troubleshoot the Furnace
- 11 Real Haunted Houses to Visit--If You Dare!
- 9 Alternative Uses for Toothpaste
- 133 Smart Storage Ideas for the Whole House
- 16 New Ways to Store Kitchen Necessities
- 8 Ways to Make a Small Room Look Big
- 21 Expert Picks for Fail-Safe Colors
- 10 Fall Door DIYs for the Best House on the Block
- The Cheapest Ways to Boost Home Value
- 10 New Uses for Old Doors
- 10 Unexpected Uses for Spray Paint
- 8 Unique Ways to Build Your Own Table
- Woodworking for Beginners: 10 Projects
- 8 Amazing Handmade Kitchen Counters
- 10 New Uses for Old Dressers
- 7 Upgrades You Can Do in Under 300 Seconds
- 10 Thrifty DIY Ways to Organize Your Home
- 26 Easy Painted Pumpkins for Halloween
- 9 Totally Amazing Mobile Home Makeovers
- 5 "Make in a Weekend" Bookshelf Projects
- 9 Decorating Lessons We Learned from Social Media
- 10 "Zero Dollar" Storage Hacks
- 121 DIY Ideas for Halloween
- The 10 Best Things to Buy Secondhand
- 16 Must-See Coffee Tables You Can DIY—Easily!