GFCI tripping when anything downline is used.
I just installed a GFCI receptacle in my bathroom and at the same time I'm replacing an old light switch and another receptacle downline from the new GFCI. For some reason the GFCI trips when anything is plugged in the downline receptacle or if the light switch is switched on. Somehow I'm just not wiring it properly, but I'm at a loss. Attached is a photo of the array of wires in the switch/outlet combo. There are 2 neutrals, a red that is tied in with a black and two blacks split from one. Any ideas? Thanks very much.
- 15 Old House Features We Shouldn't Abandon
- 17 Tiny Bathrooms We Love
- 16 Designs for a Low-Cost DIY Coffee Table
- Insanely Easy 60-Minute Home Improvements
- 12 Sheds You Could Live (or Work) In
- Assembly Required: 15 DIY Kit Homes
- 30 Things Every Adult Should Know How to Do
- 10 Surprisingly Simple Woodworking Projects
- 7 Surprising Other Uses for Mayonnaise
- 9 Ways to Make Your TV Look at Home
- 9 Totally Amazing Mobile Home Makeovers
- 8 Cleaning Mistakes Everyone Makes
- 10 Insanely Creative Shelves You Can DIY
- 10 Bargain Organizers for a Tidy Garage
- 7 Easy Budget-Friendly Backyard Makeovers
- 9 Backyard Fire Pits You Can Afford
- 10 Things You Didn't Know Windex Can Do
- Watch These 10 Home Trends Take Off in 2015
- Surprisingly Simple Woodworking Projects
- 16 Garden Borders You Can Make—Easily!